- Piping and instrumentation diagram
A piping and instrumentation diagram/drawing (P&ID) is a diagram in the process industry which shows the piping of the process flow together with the installed equipment and instrumentation.
Contents and Function
A piping and instrumentation diagram/drawing (P&ID) is defined by the Institute of Instrumentation and Control as follows:
- A diagram which shows the interconnection of process equipment and the instrumentation used to control the process. In the process industry, a standard set of symbols is used to prepare drawings of processes. The instrument symbols used in these drawings are generally based on International Society of Automation (ISA) Standard S5. 1.
- The primary schematic drawing used for laying out a process control installation.
P&IDs play a significant role in the maintenance and modification of the process that it describes. It is critical to demonstrate the physical sequence of equipment and systems, as well as how these systems connect. During the design stage, the diagram also provides the basis for the development of system control schemes, allowing for further safety and operational investigations, such as the hazard and operability study (HAZOP).
For processing facilities, it is a pictorial representation of
- Key piping and instrument details
- Control and shutdown schemes
- Safety and regulatory requirements
- Basic start up and operational information
List of P&ID items
- Instrumentation and designations
- Mechanical equipment with names and numbers
- All valves and their identifications
- Process piping, sizes and identification
- Miscellanea - vents, drains, special fittings, sampling lines, reducers, increasers and swagers
- Permanent start-up and flush lines
- Flow directions
- Interconnections references
- Control inputs and outputs, interlocks
- Interfaces for class changes
- Computer control system input
- Identification of components and subsystems delivered by others
Identification and Reference Designation
The P&ID is used for the identification of measurements within the process. Identification letters for measurements are based on Standard S5. 1 and ISO 14617-6:
First-Letter Measurement A Analysis B Burner, Combustion C User's Choice (usually Conductivity) D User's Choice (usually Density) E Voltage F Flow G User's Choice H Hand I Current J Power K Time, Time Schedule L Level M User's Choice N User's Choice (usually Torque) O User's Choice P Pressure Q Quantity R Radiation S Speed, Frequency T Temperature U User's Choice (usually Alarm Output) V Vibration, Mechanical Analysis W Weight, Force X User's Choice (usually on-off valve as XV) Y Event, State, Presence Z Position, Dimension
For reference designation of any equipment in industrial systems the standard IEC 61346 (Industrial systems, installations and equipment and industrial products — Structuring principles and reference designations) can be applied. For the function Measurement the reference designator B is used, followed by the above listed letter for the measured variable.
For reference designation of any equipment in a power station the KKS Power Plant Classification System can be applied.
Symbols of chemical apparatus and equipments
Below are listed some symbols of chemical apparatus and equipment normally used in a P&ID, according to DIN 30600 and ISO 14617.
Symbols of chemical apparatus and equipment Pipe Thermally insulated pipe Jacketed pipe Cooled or heated pipe Jacketed mixing vessel (autoclave) Half pipe mixing vessel Pressurized horizontal vessel Pressurized vertical vessel Pump Vacuum pump or compressor Bag Gas bottle Fan Axial fan Radial fan Dryer Packing column Tray column Furnace Cooling tower Heat exchanger Heat exchanger Cooler Plate & frame heat exchanger Double pipe heat exchanger Fixed straight tubes heat exchanger U shaped tubes heat exchanger Spiral heat exchanger Covered gas vent Curved gas vent (Air) filter Funnel Steam trap Viewing glass Pressure reducing valve Flexible pipe Valve Control valve Manual valve Back draft damper Needle valve Butterfly valve Diaphragm valve Ball valve
- Commons:Category:Chemical engineering symbols - A list of P&ID symbols in SVG format
- Process flow diagram
Wikimedia Foundation. 2010.