- Voltage spike
In electrical engineering, spikes are fast, short duration electrical transients in voltage (voltage spikes), current (current spike), or transferred energy (energy spikes) in an electrical circuit.
Fast, short duration electrical transients (
overvoltages) in the electric potentialof a circuit are typically caused by
* power outages
* power transitions in other large equipment on the same power line
* malfunctions caused by the power company
electromagnetic pulses (EMP) with electromagnetic energy distributed typically up to the 100 kHz and 1 MHz frequency range.
* Inductive spikes
In the design of critical infrastructure and military hardware, one concern are pulses produced by
nuclear explosions , whose nuclear electromagnetic pulse (NEMP) distribute large energies in frequencies from 1 kHz into the Gigahertz range through the atmosphere.
The effect of a voltage spike is to produce a corresponding increase in current (current spike). However some voltage spikes may be created by current sources. Voltage would increase as necessary so that a constant current will flow. Current from a discharging
inductoris one example.
electronics, excessive current can flow if this voltage spike exceeds a material's breakdown voltage, or if it causes avalanche breakdown. In semiconductorjunctions, excessive electrical current may destroy or severely weaken that device. An avalanche diode, transient voltage suppression diode, transil, varistor, overvoltage crowbar, or a range of other overvoltageprotective devices can divert (shunt) this transient current thereby minimizing voltage.
While generally referred to as a voltage spike, the phenomenon in question is actually an energy spike, in that it is measured not in
volts but in joules; a transient responsedefined by a mathematical product of voltage, current, and time.
Voltage spike may be created by a rapid buildup or decay of a magnetic field, which may induce energy into the associated circuit. However voltage spikes can also have more mundane causes such as a fault in a
transformeror higher-voltage (primary circuit) power wires falling onto lower-voltage (secondary circuit) power wires as a result of accident or storm damage.
Voltage spikes may be longitudinal (common) mode or metallic (normal or differential) mode. Some equipment damage from surges and spikes can be prevented by use of surge protection equipment. Each type of spike requires selective use of protective equipment. For example a longitudinal mode voltage spike may not even be detected by a protector installed for normal mode transients.
Uninterruptible power supply
Wikimedia Foundation. 2010.